The transformer is an extremely important element in electrical systems. So its monitoring is necessary for the continuity of the power supply and stability of electrical networks. However, the currently used frequency response analysis (FRA) is a useful tool which can give an indication of different mechanical deformations that can appear in transformer windings [1,2,3,4,5]. Furthermore, applying the FRA idea to evaluate the transformer windings state is based on the fact that the winding displacement or deformation changes according to the geometrical properties of the windings, which are related to its capacitive and inductive parameters. Changes in these parameters therefore modify the winding frequency response, which can be observed by measuring its transfer function. In the FRA process the transformer can be modeled by a complex network of RLC elements that are composed of resistances, inductances and capacitances [6,7,8,9]. In the literature, several studies suggest techniques for shape analyzing of the FRA response in order for the detection and localization of various incipient faults in the transformer windings [1, 10,11,12,13,14,15].
Therefore, a low and high-frequency behavior study of transformer windings is necessary, which will allow us to develop an equivalent model to the three-phase transformer from FRA data measurements obtained in a wide frequency range reflecting the electric and electromagnetic behavior of transformer windings. However, since the proposed model by Wilder Herrera et al. in reference  is limited to the low frequency (10 Hz-10 kHz) for studying the magnetic behavior of a three-phase transformer. Then, it is noted that the high-frequency behavior impedance of the transformer is characterized by several resonance points due to inductive and capacitive effects of the windings. This leads us to a reflection on a high-frequency equivalent model to a three-phase transformer composed of a cascade of the parallel RLC cells, whose parameters are calculated as a function of the resonance points and the bandwidth of each peak of the FRA response. The proposed model in this paper can simulates qualitatively and/or quantitatively the transformer windings behavior in the low and high frequency. The obtained results are experimentally tested on a 300 VA laboratory transformer.
2 The proposed model
An inspection of the winding impedance behavior that is characterized by several resonant points induces a reflection on an electrical model indicating their behavior, so that the different impedance peaks will be reproduced in their respective frequencies. In this work, the procedure for calculating of the three-phase transformer parameters is presented. Next, the RLC cells model method was used to estimate the transfer function of the transformer windings in order to study its frequency behavior. Figure 1 shows the FRA test performed on the phase U to obtain ZmU as a function of frequency, and thus ZmV and ZmW have been found . Hence, Figure 2 depicts the comparison between these measured impedances on each phase.
According to Figure 2, we can see that the measured impedances curves of two lateral phases (ZmU and ZmW) and that of the central phase (ZmV) are substantially same at high frequency. Whereas, it has been found at low frequency that the impedance amplitude of the first resonance of the central phase (ZmV) is greater than the other two with a shift to the left compared to the measured impedances in lateral phases (ZmU and Zm) as illustrated in Figure 2. This can be explained by the magnetic influence of the two lateral phases on the central phase.
Analysis of these tests on a wide frequency range will provide a simple electrical equivalent model to the three-phase transformer. This model is constituted of a cascade of parallel RLC cells reflecting the behavior of the transformer in low and high frequency. In addition, the three phases of the transformer can be represented by the three impedances ZU, ZV and ZW as in Figure 3. In where ZU, ZV and ZW are impedances reflecting the physical behavior of the phases U, V and W respectively. The impedances ZU, ZV and ZW are obtained using the expressions (1)-(3) from the measured impedances ZmU, ZmV and ZmW .
The series model of parallel RLC cells is based on FRA data measurement performed on a transformer winding (Figure 2). However, the parallel RLC circuits that make up the model are determined from the resonance peaks corresponding to the different cutoff frequencies of the winding response in the frequency regime. These cells, thus obtained are arranged as a function of the number of resonance points of the frequency response impedance in order to obtain the equivalent model to the winding as in Figure 4. In the cascade model of parallel RLC cells, each cell is composed by RLC elements in parallel, in which the number of cells connected in series depends on the number of measured resonance points in FRA test. Therefore, Figure 4 shows k RLC cells in series, where, each cell is composed of a resistance Rk, a capacitance Ck and an inductance Lk in parallel, with k = 1, 2, 3… In addition, the determination of equivalent circuit parameters is performed according to the flowchart of Figure 5 .
3 Synthesis of the proposed model
The proposed model is synthesized using the frequency response measured on each phase according to references [15, 16]. On the other hand, the equivalent circuit construction is deducted for each phase, and it consists of a cascade of parallel RLC cells whose parameters are identified according to the flowchart of Figure 5 [17, 18].
The cells consist of three basic passive electrical elements, inductance representing the storage magnetic field, capacitance representing the electric field storage and resistance representing the dielectric losses [17,18,19]. Otherwise, obtaining the electrical parameters; R, L and C of each cell was made from the measured frequency response for which there were several peaks throughout the frequency bandwidth. Thus, Figure 6 shows the equivalent model of the three-phase transformer.
The physical behaviors of the transformer coils as in Figure 7 were obtained for each phase using equations (1)-(3). Where the magnetic behavior can be observed at low frequency about 20 Hz-5 kHz, an increase of the central phase impedance (ZU) compared to those of the lateral phases (ZV and ZW) can be explained by the influence of these two windings on the central winding. However, ZU and ZW impedance curves are almost confused, with a slight difference due to the male manufacturing of the transformer coils. On the other hand, the procedure for diagnosing transformer failures in the FRA domain is usually based on the comparison between two FRA traces in the frequency regime, one corresponding to the transformer in the healthy state and the other of the transformer in a state of possible failures. Consequently, in order to use this model for the detection and localization of the three-phase transformer faults, two measurements of the frequency response on a healthy and defective transformer are necessary. However, each FRA measure must be modeled separately to determine the model parameters using the algorithm explained above (flowchart of Figure 5). However, the changes analysis of both parameters models of the healthy and defective transformer can give an indication of the type and the point of the defects. In addition, the percentage changes between both models parameters can be calculated [20,21,22] to find a correlation between the proposed model parameters and the fault type.
4 Experimental validation of the proposed model
The proposed model was experimentally validated on a 300 VA laboratory transformer. So that, the measurement was done automatically using the following equipment: Precision LCR meter DC, 20 Hz-5 MHz as in Figure 8.
The equivalent circuit of the three-phase transformer depicts in Figure 6, whose parameters are identified using FRA data measurements. The results obtained from the measurements on the three-transformer are compared to those estimated using the RLC cells method and shown in Figure 9(a), (b) and (c).
The model parameters were identified for each transformer phase using the RLC cells method explained in Figure 5.These parameters are shown in Table 1. However, the magnetic effect appears on the model parameters in low frequency range between 20 Hz and 1 kHz, in which the magnetic influence of the two lateral phases on the central phase can appear on the resistance and inductance values of the first peak. Besides, the inductance and resistance values of the central phase are greater than those of the lateral phases which are nearly equal (LV > LU ≈ LW and RV > RU ≈ RW) at low frequency. Otherwise, at high frequency, these parameter values (R and L) are close with certain difference due to the male manufacturing of the transformer coils. On the other hand, the electric effect of the transformer windings is represented by the capacitances that appear in the high frequency. In which we can see from Table 1 that the capacitance of the central phase is greater than that of the lateral phases (CV > CU ≈ CW). In contrast all capacitances of each phase are almost equal at low frequency (CU ≈ CV ≈ CW). Consequently, the diagnostic capability of transformer core defects can be done at the low frequency, so the deformation and/or displacement of the transformer windings can be analyzed at high frequency using the proposed model from their impact on inductive and capacitive properties. The parameters of the proposed equivalent model to a three-phase transformer are very sensitive to the geometrical changes of the transformer windings. Therefore, the existence of a minor mechanical deformations or a wrong manufacturing of the windings cause a misalignment on the model parameters.
In this paper, a modeling approach to three-phase transformer has been performed on the basis of simple low-power tests. The proposed model in this study consists of a series of parallel RLC cells, where these parameters are identified as a function of the resonance points and the bandwidth of the FRA response obtained on each transformer phase. In addition to that, the magnetic and electric behavior of the transformer coils was analyzed on the basis of the FRA response obtained on each phase and the parameters of the proposed model. Finally, this model was experimentally validated on a 300 VA laboratory transformer.
Pham D.A.K., Pham T.M.T., Gockenbach E., Borsi H., Application of a new method in detecting a mechanical failure associated with series capacitance change in a power transformer winding, IEEE International Conference on Liquid Dielectrics, (June 30 - July 3, 2014, Bled, Slovenia), Bled, 2014, 1-4. Google Scholar
Secue J.R., Mombello E., Sweep frequency response analysis (SFRA) for the assessment of winding displacements and deformation in power transformers, Electric Power Systems Research, 2008, 78, 1119-1128. Web of ScienceCrossrefGoogle Scholar
Bagheri S., Efftnejad R., Salami A., Transformer Winding Parameter Identification based on Frequency Response Analysis using Hybrid Wavelet Transform (WT) and Simulated Annealing Algorithm (SA) and Compare with Genetic Algorithm (GA), Indian Journal of Science and Technology, 2014, 7, 614-621. Google Scholar
Abu-Siada A., Frequency response analysis using high frequency transformer model, Elixir Elec. Eng., 2011, 41, 5827-5831. Google Scholar
Hossein S.M.H., Adineh H.R., Saeedi M., Improved Modeling of Power Transformer Winding Using PSO, International Journal of Engineering and Innovative Technology, 2013, 3, 455-459. Google Scholar
ArulSathya M., Usa S., Prediction of Changein Equivalent Circuit Parameters of Transformer Winding Due to Axial Deformation using Sweep Frequency Response Analysis, Journal of Electronic Engineering and Technology, 2015, 10, 983-989. CrossrefGoogle Scholar
Islam S.M., Coates K.M., Ledwich G., Identification of high frequency transformer equivalent circuit using Matlab from frequency domain data, Industry Applications Conference, Thirty- Second IAS Annual Meeting, IAS ’97, (5-9 Oct, 1997, New Orleans, USA), 1997, 357-364. Google Scholar
Chaouche M.S., Houassine H., Moulahoum S., Colak I., Finite element method to construct a lumped parameter ladder network of the transformer winding, Renewable Energy Research and Applications (ICRERA), 2017 IEEE 6th International Conference, (5-8 Nov, 2017, San Diego, USA), San Diego, 1092-1096. Google Scholar
Shintemirov A., Tang W.H., Wu Q. H., Transformer winding condition assessment using frequency response analysis and evidential reasoning, IET Electric Power Applications, 2010, 4, 198-212. Web of ScienceCrossrefGoogle Scholar
Ragavan K., Satish L., Localization of Changes in a Model Winding Based on Terminal Measurements: Experimental Study. IEEE Transactions on Power Delivery, 2007, 22, 1557-1565. CrossrefWeb of ScienceGoogle Scholar
Islam A., Khan S.I., Hoque A., Detection of Mechanical Deformation in Old Aged Power Transformer Using Cross Correlation Coefficient Analysis Method, Energy and Power Engineering, 2011 3, 585-591. CrossrefGoogle Scholar
Karimifar P., Gharehpetian G. B., A new algorithm for localization of radial deformation and determination of deformation ex tent in transformer windings, Electric Power Systems Research, 2008, 78, 1701-1711. CrossrefGoogle Scholar
Chaouche M.S., Houassine H., Moulahoum S., Colak I., Faults Investigation of Transformer Windings Using the Frequency Response Analysis FRA. 15th IEEE International Conference on Machine Learning and Applications, (18-20 Dec, 2016, Anaheim, USA), Anaheim, 452-459. Google Scholar
Chaouche M.S., Moulahoum S., Houassine H., Three phase transformer modelling by frequency response analysis measurement, 18th IEEE International Symposium on Electromagnetic Fields in Mechatronics, Electrical and Electronic Engineering (ISEF) Book of Abstracts, (14-16 Sept, 2017, Lodz, Poland), Lodz, 1-3. Google Scholar
Herrera W., Aponte G., Pleite J., Gonzalez G.C., A novel methodology for transformer low-frequency model parameters identification, Electrical Power end Energy System, 2013, 53, 643- 648. CrossrefGoogle Scholar
Guimarăes R.C., Modelo Elétrico da Impedância do Transformador Baseado em Células RLC Passivas, Dissertaçăo de mestrado (Engenharia tese), 2010, Porto Alegre University. Google Scholar
Villacián C.C., Aportaciones al modelado del transformador en alta frecuencia, (PhD thesis), 2012, Cantabria University. Google Scholar
Gonzalez G.C., Procedimiento de Modelado basado en el Análisis de la Respuesta en Frecuencia y aplicación en Transformadores Trifásicos de Potencia para su Caracterización y Diagnóstico, (PhD thesis), 2012, Leganés University. Google Scholar
Aponte G., Cadavid H., Martinez J., Castańo J., Herrera W., Evaluación de la Respuesta en Frecuencia del Transformador utilizando un modelo Circuital de Celdas. Revista Energía y Computación, 2010, 18, 1-8. Google Scholar
Aponte G., Herrera W., Gonzalez-G. C., Pleite J., Implementación de un Modelo de un Transformador Eléctrico para el Análisis de su Respuesta en Frecuencia, Información Tecnológica, 2011, 22, 59-72. Google Scholar
Pleite J., Olías E., Barrado A., Lázaro A., Vázquez J., Modeling the transformer frequency response to develop advanced maintenance techniques, 14th Power Systems Computation, (24-28 June, 2002 Sevilla, Spain), Sevilla, 2002, 1-6. Google Scholar
About the article
Published Online: 2018-04-18
Citation Information: Open Physics, Volume 16, Issue 1, Pages 117–122, ISSN (Online) 2391-5471, DOI: https://doi.org/10.1515/phys-2018-0019.
© 2018 Moustafa Sahnoune Chaouche et al.. This work is licensed under the Creative Commons Attribution-NonCommercial-NoDerivatives 4.0 License. BY-NC-ND 4.0